- rain barrels
- Packaged Systems
Downpipe First Flush Water Diverters improve water quality and reduce tank maintenance by preventing the first flush of water, which may contain roof contaminants, from entering the tank. They help ensure cleaner water is available for use, which protects rainwater pumps and internal household appliances such as clothes washing machines, toilets, hot water systems, etc.
Downpipe First Flush Diverters, such as the 3" and 4" round kits, are installed at each downpipe that supplies water to the tank. They utilize a dependable ball and seat system - a simple automatic system that does not rely on mechanical parts or manual intervention. As the water level rises in the diverter chamber, the ball floats, and once the chamber is full, the ball rests on a seat inside the diverter chamber preventing any further water entering the diverter. The subsequent flow of water is then automatically directed along the pipe system to the tank.
Fitting an appropriately sized First Flush Water Diverter is critical to achieve good quality water. Water Diverters improve water quality, reduce tank maintenance and protect pumps by preventing the first flush of water, which may contain contaminants from the roof, from entering the tank.
When it rains, water slowly builds up in the roof guttering system before it exits through the downpipe. The first flush of water from the roof can contain amounts of bacteria from decomposed insects, skinks, bird and animal droppings and concentrated tannic acid. It may also contain sediments, water borne heavy metals and chemical residues, all of which are undesirable elements to have in a water storage system.
Instead of flowing to the water tank, these pollutants are diverted with the initial flow of water into the chamber of the water diverter. The water diverters from Rain Harvesting utilise a dependable ball and seat system - a simple automatic system that does not rely on mechanical parts or manual intervention.
As the water level rises in the diverter chamber the ball floats, and once the chamber is full, the ball rests on a seat inside the diverter chamber preventing any further water entering the diverter. The subsequent flow of water is then automatically directed along the pipe system to the tank.
For a water diverter to work effectively, the contaminated water in the chamber must be sealed off. This prevents the water passing to the storage tank and ensure the water does not "syphon" off the contaminated water in the chamber. The simplest and surest way to do this is with a floating ball and seat.
A slow release valve ensures the chamber empties itself after rain and resets automatically. The diverted water need not be wasted water because the drain pipe from the diverter chamber can be fitted to a standard drip irrigation system.
It is important to prevent heavy sediments and other roof pollutants from entering the rainwater tank. The amount of water diverted should be a minimum of 5 gallons per 1000 square feet of roof area. In calculating the amount of water to divert, consideration can be given to (1) the surface area of the roof, and (2) the amount of pollutants on the roof and gutters.
As a rule of thumb, the more water that is diverted the better the quality of water in the tank/cistern.
1. Determine the length of Diverter Chamber #4. Consider as a guide
– 3 foot section of 3″ Schedule 40 PVC pipe holds approx. 1.5 gallons
– 3 foot section of 4″ Schedule 40 PVC pipe holds approx. 2 gallons of
Fit the longest length of pipe possible, making sure the Screw Cap
#10 is at least 6″ from the ground to allow for removal and
2. Place the ball Seat #9 into the Tee Junction #6 ensuring the narrow
end of the ball seat points down into the Diverter Chamber #4. Apply
glue to the Diverter Chamber #4 and fit up against the Ball Seat #9
and hold until the glue sets. (Optional: Use a 45º bend adaptor to
allow easier removal of the Screw Cap #10). Glue the Socket #14 to
the bottom end of the Diverter Chamber #4.
3. Fix the assembled chamber directly to the wall in the desired position
using the Wall Brackets.
4. Connect a Male & Female (M&F) Elbow #8b (if required) to the
Chamber Outlet #8 and connect the downspout #3. Fit an elbow to
the InFeed pipe #2 (if required) and connect to the bottom of the
selected rain head.
5. Select the appropriate Flow Control Valve #11 and insert into the
Hose Connector #16, making sure the valve is inserted with the side
marked “TOP” still showing. Start by using the Control Washer with
the smallest gauge hole (lowest number). Try a larger gauge Washer
if experiencing blockages. Place the Filter Screen #13 into position
from the outside of the Screw Cap #10 and then attach the Hose
An extra filter screen that helps stop the Control Valve blocking is
available from your local store. Ask for the “Optional Stainless Steel
Primary Screen” (Product Code: WDAC02). This filter is fitted in
addition to the Plastic Filter Screen #13. To install: After completing
step 5, insert the Keeper Ring #1a into the Screen Cap #10 and then
place the Optional Stainless Steel Primary Screen on top of the Keeper
Ring #1a. Proceed to step 6.
6. Place the Sealing Ball #5 into the Diverter Chamber #4 and attach the
assembled Screw Cap #10 to the Socket #14.
Completed the total installation of the 3" First Flush diverter system as well as a leaf eater as a "Y" type downspout. All told it took about a half day to do so as I had to go get a piece of 3" PVC as well as fittings glue etc and took many breaks, never get in a hurry I always say. We had a light rain the evening we finished up and collected about 5" of rainwater in our 330 gallon tank, the next morning our tank was full. Thanks Rainbrothers for a great economical product.
terry on 23rd Apr 2018